bartbakels wrote:hi i have a similair questions,
I have an x10 system in house with x10 PC interface. I bougt some plcbus inwall 1 load 2267 modules and a 4808 unit. Can i use those inwall switches with my x10 controller by using the 4808? I dont have any plcbus transmitters.
If you are using One Phase system , so you only need one unit of PLCBUS-4808. ((PLCBUS-4808 need to be set in 1 Phase Mode)
Since PLCBUS-4808 will "translate" X10 to PLCBUS and also "translate" PLCBUS to X10.
But if you are using Three Phase System , that will be complicated.
Case 1) If all the PLCBUS receiver (PLCBUS Wall Switch , PLCBUS Micro Module , PLCBUS Plug-in module) all in the same phase , so you need :
X10 Coupler + one unit of PLCBUS-4808 that plug in the same phase of your PLCBUS receiver (PLCBUS-4808 need to be set in 3 Phase Mode)
Case 2) If you only have one X10 controller and PLCBUS receiver across different phase , so you need :
X10 Coupler + PLCBUS Coupler , and only need one unit of PLCBUS-4808 and plug into the same phase of your X10 controller (PLCBUS-4808 need to be set in 3 Phase Mode)
Case 3) If you have many X10 controller in three different phase , so you need :
X10 Coupler + PLCBUS Coupler + Three unit of PLCBUS-4808 (PLCBUS-4808 need to be set in 3 Phase Mode)